[802.3af] AW: Liaison report from ISO/IEC JTC 1 SC 25/WG 3 on mid-span power insertion
thanks for this quick answer that - if complete and future proof - makes
life much easier.
But to be on the safe side, let me confirm explicitly: there is no need for
us to consider mid-span-power insertion for applications using all four
pairs for information transfer.
Von: Geoff Thompson [mailto:gthompso@xxxxxxxxxxxxxxxxxx]
Gesendet am: Sonntag, 10. März 2002 06:31
An: Pattay Walter
Cc: Alan Flatman; scarlson@xxxxxxxxxxxxx; thompson@xxxxxxxx;
Betreff: Re: Liaison report from ISO/IECJTC 1 SC 25/WG 3 on mid-span power
We will review your Liaison at our meeting in St. Louis during the upcoming
Re: your text on the cover of the Liaison Letter:
Due to the discussion in Kyoto it would be important for WG 3 to
know whether mid-span power insertion will always use separate
pairs, that is pairs which are not used for information transfer or
whether there is also a need to provide this function for pairs used
for information, e. g. when only two pairs are terminated at the TO.
The next meeting of WG 3 will take place near Washington,
D.C., USA, 2002-09-23/26.
The answer to the above question is as follows:
Mid-span will always use separate pairs.
End-to-end may use either the data pairs or the "separate pairs" but not
Therefore, mid-span may not be used in a situation where only 2 pairs are
terminated at the TO
I hope to be able to attend the upcoming meeting in the Washington, D.C.
At 11:36 AM 3/6/02 +0100, you wrote:
please receive the liaison report as it was approved at our last meeting.
Unluckily we were short of time - as usual - and not all the output already
created on this subject was found complete or ripe enough to be forwarded
to you in this report.
We definitely will do some more work on this subject at our next meeting. As
the outcome may be an interface to generic cabling in addition to those
defined in the present model, it promises to be a challenging subject.
Hoping to see you there again I remain with best wishes